Secutron’s MRM-710(U) Series Manual Pull Station provides manual fire reporting. This high quality, die-cast metal manual station is a dual action unit with SPST contacts and terminal strip connections. The normally open contact, which closes when the manual station is activated, is rated for 1 amp, 30 VDC. The contacts are gold plated to avoid the risk of corrosion. The MRM-710(U) Series Manual pull stations is available with CAT-30 lock and keys and mounts on a standard single gang backbox, Secutron’s MRM-700 surface metal backbox or MRM-700WP weatherproof backbox.
The MRM-710(U) Series Manual pull stations is listed for outdoor applications when used with the MRM-700WP.
The MRM-710(U) Series Manual pull stations is operated by pushing the bar and then pulling down the handle on the front of the station. The unit is reset by opening the station with the key, placing the handle in the normal upright position and relocking the station.
The manual station shall be Secutron’s MRM-710(U) Series Manual pull stations. Operating instructions shall be in raised English or English and French lettering and the unit shall be constructed of high quality die-cast metal and finished in red enamel paint to provide quick identification. Pulling the handle shall initiate immediate operation of the alarm detection circuit.
All manual fire alarm stations shall be installed as per the specific requirements outlined in the UL codes, as well as all other applicable national or local codes. Final acceptance is subject to the local authority having jurisdiction.