The normally open contact, which closes when the manual station is activated, is rated for 1 amp, 30 VDC. The contacts are gold plated to avoid the risk of corrosion.
The MRM-710U is available with CAT-30 lock and keys and mounts on a standard single gang backbox, Secutron’s MRM-700 surface metal backbox or MRM-700WP weather proof backbox.
The MRM-710U Manual Station is listed for outdoor applications when used with the MRM-700WP
(N.O. Contact w/ Station Closed)
The MRM-710U Dual Action Manual Station is operated by pushing the bar labelled “PUSH BAR” and then pulling down the handle marked “PULL HANDLE”. The MRM-710U Manual Station is reset by opening the station with the key, placing the handle in the normal upright position and re-locking the station.
The manual station shall be Secutron’s MRM-710U. Operating instructions shall be in raised English lettering and the unit shall be constructed of high quality die-cast metal and finished in red enamel paint to provide quick identification. Pulling the handle shall initiate immediate operation of the alarm detection circuit. All manual fire alarm stations shall be installed as per the specific requirements outlined in the UL codes, as well as all other applicable national or local codes. Final acceptance is subject to the local authority having jurisdiction.