Attractive and durable, Secutron’s MRM-MPG Series manual station provide manual fire reporting. The MRM-MPG Series manual stations are non-coded, single action device which initiates an alarm when pulled. Resetting is accomplished by inserting a 1/8” screwdriver from the front.
The handle, once pulled will remain open and cannot be reset without utilizing the screwdriver.
The MRM-MPG Series manual stations are constructed of durable aluminum and finished in red. An abrasion resistant label with large, raised letters provides clear legible instructions.
Pulling on the station’s handle will release the internal switch to trigger the alarm detection circuit. The MRM-MPG Series Manual Stations are available in many different configurations. The MRM-MPG1U & MRM-MPG1A are a single action, single stage manual
station. The MRM-MPG2U & MRM-MPG2A are two stage and contain an additional General Alarm (G.A.) N.O. switch. For safety reasons, the G.A. switch is only accessible after the handle has been pulled. A special key is supplied with each unit.
The single action manual station shall be Secutron’s MRM-MPG Series. Operating instructions shall be in raised English lettering and the unit shall be constructed of extruded aluminum, finished in red enamel paint to provide quick identification. Pulling the handle shall initiate immediate operation of the alarm detection circuit. All manual fire alarm stations shall be installed as per the specific requirements outlined in the UL/ULC codes, as well as all other applicable national or local codes.