Secutron’s MRM-400MP(U) Series Fire Alarm Manual Stations provide manual fire alarm activation. They are constructed of high quality, extruded aluminum and finished in red.
An abrasion resistant label with large, raised letters provides clear legible instructions.
Pulling on the station’s handle will release the internal switch to trigger the intelligent addressable module.
Resetting is accomplished by inserting a 1/8” screwdriver from the front. The handle, once pulled will remain open and cannot be reset without utilizing the screwdriver.
The single action manual station shall be Secutron’s MRM-400MPU Series. Operating instructions shall be in raised English lettering and the unit shall be constructed of extruded aluminium, finished in red enamel paint to provide quick identification. Pulling the handle shall initiate immediate operation of the alarm detection circuit. All manual fire alarm stations shall be installed as per the specific requirements outlined in the UL/ULC codes, as well as all other applicable national or local codes.
ATTENTION: To set the address on this device, disconnect it from the loop, or ensure that the loop to which it is connected is both disconnected from the panel and shorted across the SLC+ and SLC− inputs at the device. Failing to take either of these steps may change the address programming of previously configured sensors on the same loop.